IC controlled Dual rate Charger for energy savings.
Short circuit protection at battery terminals.
Battery reverse protection functionality
Charge indicator and test button. The light fittings guarantee safety of people in buildings open to the general public.
Automatically actuated in the event of power cuts, these devices (kit + light fitting) offer a good luminous flux to facilitate the evacuation.
Comply with European standards EN 61 347-2-7 and offer a high level of quality and safety meeting the various prevailing regulations.
Dial the code to suitable voltage of luminiares.
1 or 3 h rated duration
Constant current output,emergency power is vaired by lighting output voltage, automatically match with the lighting setting to provide best illuminations.
Emergency Module for LED Panels/LED Lighting Panel Emergency Conversion Kit
1.The battery charging and discharging times:>500 times;
2.Ambient Temperature range ta:0°C~+55°C
3.Max.casing temperature tc:70°C
4.Test button and green indicator: out 30cm length
5.Battery:Ni-cd 7.2V 2.0AH
6.Emergency power: 4-5W
7.LED Light : 40/36W LED Panel
9.DC connectors outside 30cm length
2. Connecting installation
2.1. It is strictly connected the circuit according to the connecting diagram. Each terminal connects the following circuits:
N - connect neutral wire, N + LED built-out driver neutral line input terminal.
L - connect live wire, L + LED built-out driver neutral line input terminal, set up a wall switch - K, the wall switch only control AC illumination, not effect emergent lighting.
9 - connect luminaire positive terminal.
10 - connect luminaire negative terminal + LED built-out driver output negative terminal.
12 - luminaire built-out driver output positive terminal.
White socket - connect batteries.
3. Installation matters
It is strictly connected the circuit according to the connecting diagram, distinguish the neutral wire from the live wire.
Electricity-free when conducting a connection by an electrical technician.
The wall switch only controls the AC, not the emergent power.
AC illumination and emergent illumination don’t permit no-load working.
Chief electric box derives an emergent circuit, not to load switch in the middle way.
Emergent specialized circuit voltage is 220V/50HZ.
Screw up the wire terminal when connecting, draw down the wire to check its tightness.
Different colors distinguish from different circuits to guarantee an easy connection.