Emergency Module for LED Panels/LED Lighting Panel Emergency Conversion Kit
1.The battery charging and discharging times:>500 times;
2.Ambient Temperature range ta:0°C~+55°C
3.Max.casing temperature tc:70°C
4.Test button and green indicator: out 30cm length
5.Battery:Ni-cd 7.2V 2.0AH
6.Emergency power: 4-5W
7.LED Light : 40/36W LED Panel
9.DC connectors outside 30cm length
2. Connecting installation
2.1. It is strictly connected the circuit according to the connecting diagram. Each terminal connects the following circuits:
N - connect neutral wire, N + LED built-out driver neutral line input terminal.
L - connect live wire, L + LED built-out driver neutral line input terminal, set up a wall switch - K, the wall switch only control AC illumination, not effect emergent lighting.
9 - connect luminaire positive terminal.
10 - connect luminaire negative terminal + LED built-out driver output negative terminal.
12 - luminaire built-out driver output positive terminal.
White socket - connect batteries.
3. Installation matters
It is strictly connected the circuit according to the connecting diagram, distinguish the neutral wire from the live wire.
Electricity-free when conducting a connection by an electrical technician.
The wall switch only controls the AC, not the emergent power.
AC illumination and emergent illumination don’t permit no-load working.
Chief electric box derives an emergent circuit, not to load switch in the middle way.
Emergent specialized circuit voltage is 220V/50HZ.
Screw up the wire terminal when connecting, draw down the wire to check its tightness.
Different colors distinguish from different circuits to guarantee an easy connection.